Question about Heating & Cooling
Roll out occurs if there is not enough combustion air at the burners or there is a blockage of the vent pipe. check both for problem. a blocked heat exchanger can also cause a roll out.
Posted on Oct 11, 2010
Testimonial: "As you and I both suspected, the vent pipe had a nest in it, All set. Thanks"
It still could be the heat exchanger because it causes back draft pressure in the combustion chamber
Posted on Oct 27, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 10, 2013 | Heating & Cooling
Oct 19, 2013 | Heating & Cooling
Feb 19, 2013 | Heating & Cooling
Nov 04, 2011 | Goodman GMS90703BXA Heater
Sep 14, 2011 | Heating & Cooling
E in your model number means it is an electronic ignition...you do not have a
pilot. ROL means your flame rollout sensor is open. Either the wiring to the
sensor or the sensor itself is faulty or there is a flame rollout issue causing
the heater to shut down for good reason and the cause of the rollout needs to
be determined and corrected in order to run the heater.
replacement part for the switch is 006035F. It will need to be replaced since
one it burns open it is shot.
for flame rollout issues include blocked gas venturies on the manifold causing
a sudden and violent ignition of gas as it lights the burners or blockage of
heat and flue gas from escaping across the heat exchanger and out the top of
this answer does not fix your problem, please comment with additional details
prior to rating the answer. You may also contact me thru our website at www.arrowpools.net. Positive feedback is appreciated
once your problem is solved!
Sep 13, 2011 | Raypak 2100 Pool Heater Propane 206000...
Dec 13, 2010 | Goodman Heating & Cooling
Oct 03, 2009 | Weather King 12AJA4801AH Air Conditioner
Jun 22, 2009 | Pentair Minimax Ch 400,000 Btu Propane...
Oct 25, 2008 | Heating & Cooling
234 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: