Question about Ruud UBHC Air Conditioner
Hi, I own a RUUD home air conditioner that continues to blow fuses. It won't cool my house but the fan will come on. Any suggestions?
Fuses are a protection device and I guess that this is for the condenser section and compressor. If they blow right now when it is turned on would indicate that there is a short in the wiring or motor or compressor. If it trys to start and the outside fan starts and the compressor just humms and blows fuse, you have a locked compressor. Might check run capacitor or install a hard start kit and see if it will brake it loose, if not bad compressor
Posted on May 31, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 11, 2015 | Heating & Cooling
Jul 31, 2011 | Ruud UBHC Air Conditioner
Jul 05, 2010 | Ruud UBHC Air Conditioner
Jun 12, 2010 | Ruud UAKA018 Air Conditioner
Apr 04, 2010 | Ruud UBHC Air Conditioner
Sep 27, 2009 | Ruud UBHC Air Conditioner
Sep 21, 2009 | LG Heat cool Window Air Conditioner
Jun 14, 2009 | Ruud UBHC Air Conditioner
Jun 05, 2009 | Ruud UPMC036 Air Conditioner
May 31, 2009 | Ruud UAMB Air Conditioner
296 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: