Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
OK lets see what we can help you with here. The condensate drain is clogged. There are a couple of ways to clear this clog so lets give it a try. If you know where the drain for the a/c is located outside (usually by the outside condenser unit) it will be a pipe that is just sticking out of the side of the house, if you find it take a wet/dry vac and place it on this pipe and turn the vacuum on and make a seal with your hand this should unclog the drain. If you don't find this pipe outside the house then go to the furnace and you will see at the bottom of the furnace a pipe (PVC) white, this is the drain for the unit inside. Take the wet/dry vac and have it at the ready in the event the clog is further down the line than at the furnace itself now the fittings on this pipe should not be glued together due to the ability to access for this very purpose. Take the pipe apart at one of the fittings and place the wet/dry vac on the end of the pipe towards the furnace and using your hand make a seal and evacuate the line. Do this to both sides since you don't know where the blockage is. If you are unable to separate the pipe at any fitting you will need to cut the pipe and at the spot of the cut you will need to repair it with a sleeve. Remember that the drain pipe is plastic and is made of pvc so you can get a repair coupling from any home improvement store for this repair.
Hope this helped you some
Posted on Feb 21, 2010
When the unit heats inside, the outdoor unit cools, and if the outdoor cooling coil gets too cold the system turns off indoor fan, and changes gas flow direction to de-ice the outdoor coil. Ensure both coils, and the filters are clean and if there is still a problem check system gas pressure for leaks.
Posted on Apr 24, 2010
SOURCE: we live in a remote
You can get the service manual on the link below. It tells you what the code means on the manual and how to fix. Open the link in a new window to download it.
Posted on Aug 29, 2010
Tips for a great answer:
Dec 10, 2017 | Panasonic Microwave Ovens
Apr 28, 2015 | Panasonic CU-E18JKK-1/CS-E18JKKW-1 Wall...
Aug 17, 2011 | Heating & Cooling
Sep 12, 2009 | Heating & Cooling
Aug 21, 2009 | Panasonic Heating & Cooling
Jul 20, 2009 | Microwave Ovens
Jun 10, 2009 | Panasonic MCM INVERTER
175 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: