Question about Pentair Minimax Ch 250,000 Btu Natural Gas Pool Heater Millivolt Ignition
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
More often than not this will be the by-pass and thermal regulator. Both of these are inside the water manifold on the side of the heater. I will usually replace both if one is bad. If one is bad the other can become damaged and the labor and parts to do this are a big part of the job. Also check and see if you have a by-pass on the plumbing going to the heater. This will be a valve bridging the water in to and out of the heater. If you have one it should be 80-90% closed so it forces water through heater. If any of these are bad it will let water go past the heater and the water inside the unit will overheat and turn to steam and with no place to go it just expands and starts banging.
Posted on May 17, 2010
SOURCE: I have a minimax nt
We have this part number in stock and ready for shipping. (MANUFACTURER NUMBER: 472362) They range in price online from $399-$459.00 but since you are a FIX YA member, we offer a special discount to you. Your cost, from us, is $379.00 plus shipping. We have 2 in stock but expect there to be a pretty good run on replacement parts with the freezing across the country. Comes complete with Gasket.
If you want to search elsewhere, just put the part number in your search bar. You can reach us at: email@example.com or by calling 602-714-3880.
Posted on Feb 02, 2011
For most pool heaters, if they will not start up in the spring, the problem is corrosion in the wiring somewhere... I would remove and clean all wiring connections and then try. The amount of current is very small and so any bit of corrosion can cause the unit not to work.
It all so could the t-stat again, but you would need to check that with an OHM meter. No continuity when the heater should be on will confirm that the t-stat is bad...
Posted on May 14, 2011
Tips for a great answer:
Jul 04, 2014 | Pentair Minimax NT Heater
Jun 04, 2014 | Pentair Minimax NT Heater
Feb 16, 2012 | Pentair Minimax NT Heater
Jul 12, 2009 | Pentair MINIMAX NT TSI IGNITER
Jul 05, 2009 | Pentair MINIMAX NT TSI IGNITER
Jun 09, 2009 | Pentair Minimax NT Heater
49 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: