Question about Chicago Pneumatic Air Tools & Compressors
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Sounds like you have a bad capacitor for your squirrel cage fan , now as for the a/c unit sounds like you have a direct short in compressor to ground or leg to leg , check all wiring to make sure that it is not grounding out or melted together.
Posted on Jul 23, 2009
You could use 6/3 with ground. You must take an equipment ground conductor along with your current carrying conductors. Still drive a ground rod at the building, and add a seperate ground bar in the sub panel. Connect your equipment grounding conductor from main building along with the equipment grouding conductor to the ground rod. Do not bond the neutral in the sub panel to ground. Be aware you will still have some voltage drop, so a 220V air conditioner might be better.
Posted on Sep 24, 2010
Tips for a great answer:
Mar 01, 2017 | Car Audio & Video
Nov 17, 2011 | Square D Qo 200 Amp 40 Circuit Indoor...
Oct 03, 2010 | Siemens 100 Amp Main Breaker Renovation...
Sep 10, 2010 | General Electric GE ELECTRICAL TQD22200X2...
Oct 11, 2009 | Welding Tools
Jul 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Apr 25, 2009 | Car Audio & Video
Nov 29, 2006 | Jl Audio 1000/1 Car Audio Amplifier
Jul 05, 2015 | Chicago Pneumatic Air Tools & Compressors
May 17, 2015 | Chicago Pneumatic Air Tools & Compressors
65 people viewed this question
Usually answered in minutes!