Question about Goodman GPC1342H21A Air Conditioner
Turn the thermostat to fan only and insure you get air blowing through the registers or feel air pulling in at the return air. If YES then make sure you have the thermostat programmed correctly to call for cooling when set to auto! Also the start/run capacitor may be failed out side at the condensor unit. They are cheap to replace but dangerous to handle so becareful. If NO then you are not getting signal to the blower and may have a failed transformer that converts 120v to 24v for the thermostat controls. Also double check your breakers in your service panel to see if they tripped for some reason. A failing or weak breaker can cause this symptom aswell!
Posted on Oct 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 27, 2013 | Acura Cars & Trucks
Mar 23, 2012 | Computers & Internet
Oct 08, 2010 | Goodman GPC1342H21A Air Conditioner
Jun 10, 2010 | Panasonic Viera TH-46PZ85U Plasma TV
Mar 10, 2010 | 2003 Mini Cooper
Mar 23, 2009 | 1995 Dodge Dakota
Oct 10, 2008 | Samsung S760 Digital Camera
Aug 18, 2007 | Olympus FE-110 Digital Camera
219 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: