Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
My evcon furnace will not hold flame after eight seconds it shuts the gas off and then restarts agian over and over any help?
Most likely your flame rod is either dirty, bad or the flame is not hitting it. It is located either to the far left or far right of the burner box. It has one wire going to it and looks like a small stick pointing into the flame. Clean it with a long tooth brush. Inspect the wire where it attaches to both the rod and the control module. Inspect the flame as it starts and see if the flame reaches it within 2 to 3 seconds from first flame. If not, you may have debris clogging the flame tray not allowing the flame to pass. If this is beyond your mechanical skills (no offence) contact your gas technician.
Posted on May 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 14, 2014 | Heating & Cooling
Dec 22, 2010 | Coleman Propane Forced Air Heater...
Feb 05, 2010 | Coleman Propane Forced Air Heater...
Jan 13, 2010 | Coleman Propane Forced Air Heater...
Apr 11, 2009 | Heating & Cooling
Mar 31, 2009 | Coleman Propane Forced Air Heater...
Jan 16, 2009 | Coleman Propane Forced Air Heater...
Jan 30, 2008 | Heating & Cooling
May 15, 2014 | Coleman Propane Forced Air Heater...
154 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: