Question about Goodman Heating & Cooling
The ID Blower pressure switch may be stuck closed, and keeps the ID blower running. Replace the switch. Click on the following link for a Parts Manual for your unit to Identify the part # and order it. http://www.alpinehomeair.com/related/RP-410F%20GKS9%20Parts%20Manual.pdf
Good Luck!! Thank you for using FixYa
Posted on Oct 07, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 27, 2015 | Goodman Heating & Cooling
Nov 01, 2013 | Goodman GMS90703BXA Heater
Sep 18, 2012 | Goodman GMS90703BXA Heater
Dec 06, 2017 | Heating & Cooling
Nov 12, 2010 | Goodman GDS80904BNA Open Flame Heater
Nov 02, 2010 | Goodman Heating & Cooling
Jan 20, 2010 | Fasco GSW Hot Water Heater Exhaust Draft...
Jan 14, 2010 | Goodman GMS90703BXA Heater
Nov 23, 2008 | Goodman GMS90703BXA Heater
Nov 18, 2008 | Goodman GMS90703BXA Heater
127 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: