Question about Heating & Cooling
If it has service ports on each side of the motor you need to add Zoomspout oil to the cotton wells. Check the capacitor if you have a seperate cap for the fan motor. Look for swelling that is a sure sign of cap failure.Kill power at the outside unit before checking anything.
Posted on Oct 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 27, 2010 | Heating & Cooling
Jun 17, 2010 | Heating & Cooling
May 04, 2010 | Coleman Heating & Cooling
Mar 21, 2010 | Ruud Heating & Cooling
Jan 31, 2010 | Heating & Cooling
Jan 10, 2010 | Heating & Cooling
Jan 07, 2010 | Amana Heating & Cooling
Dec 04, 2008 | Heating & Cooling
68 people viewed this question
Usually answered in minutes!