Question about Heating & Cooling
The pressure switch, open or closed depends on the induce fan motor. the switch could of failed. Try blowing into it, in and out. And or your induce fan motor is not blowing out the excessive heat out of the furnace properly. We provide repairs in the So Cal Area.
Posted on Oct 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 30, 2015 | Heating & Cooling
Jan 01, 2015 | Heating & Cooling
Dec 17, 2013 | Heating & Cooling
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Jan 24, 2011 | Goodman Heating & Cooling
Oct 18, 2010 | Goodman GMS80453ANA Open Flame Mid-Size...
Dec 18, 2009 | York Furnace Draft Inducer Blower Fasco #...
Dec 12, 2009 | Heating & Cooling
Jan 26, 2009 | Goodman GMS90703BXA Heater
Dec 19, 2008 | Kitchen Appliances - Others
Jan 23, 2008 | Goodman GMS90703BXA Heater
Aug 21, 2017 | Heating & Cooling
172 people viewed this question
Usually answered in minutes!