Question about TORK Variable Cycling Timer 8601
Tork 1103 is mechanical timer with 125V 3 watt clock motor
Dial on front face rotates when clock has voltage
Dark and light colored pins connected to dial, and turn timer on and off
There is removable brass bar that connects poles L and 1
You have 4 wires:
Red >>> I'm not sure about this wire, is this Hot wire coming from tandem breaker?
Black >>> this is Hot wire coming from tandem breaker
White >>> this is Neutral wire
Please test Black and Red to bare ground to see if these are both Hot
Test Hots to white to confirm this is Neutral
Solution ASSUMES black and red are both Hot, and white is Neutral
You have 2 problems:
Prob 1) Clock does not rotate dial: so clock is bad -or- clock not wired correctly
Prob 2) You are able to control 4 plugs using manual override, which means load wires are correct
However, you want to wire timer 'without red wire' (which is confusing, since red wires are connected to outlets)
Solution Prob 1:
1) The diagram show the N or Neutral wire is connected to Unmarked pole on timer
2) Black Hot has to be connected to pole L
3) Unmarked pole and pole L must be wired with 120V as shown before dial will rotate
4) If wiring is correct and dial does not rotate, then clock motor is bad
5) If dial rotates, check outer rim of dial to see if you have dark and light pins for on-off functions
6) Notice that all the Neutrals connect on Unmarked pole
Are you saying that the household wiring extends beyond the 4 plugs, so when you turn off the 4 plugs, it also turns off more plugs and switches farther down the line? If so, you need to wire plugs with separate hot wire.
Let me review features on timer which might help:
1) There is removable brass bar between poles L and 1
2) If brass bar is removed, then you need Hot wires on both L and 1... but you can jumper between L and 1 with short black wire
3) If brass bar is there, then one Hot connected to either L or 1 will power both clock and load.
4) Timer is DPST double pole single throw ... so you can control 2 different loads ... one load connects to Unmarked pole and pole X ... another load connects to Unmarked pole and pole 2
If brass bar is removed:
Jumper between poles L and 1 ... so only one Hot wire is used on your timer.
Below shows jumper on poles L & 1: hot to load is on pole 2
Posted on Oct 07, 2010
I need help too! Same problem but I'm not an electrician. The one who installed the timer kept me waiting here all day and it's now 7:30 pm. I am stuck now having to try to fix this on my own. Clock timer doesn't work but I can do this manually.
Posted on Aug 06, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 19, 2014 | Woods In-Wall Digital 5-10-15-30-Minute...
May 30, 2012 | GE Hardware & Accessories
Aug 07, 2011 | Hardware & Accessories
Dec 14, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Dec 02, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Nov 06, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Oct 30, 2010 | TORK Variable Cycling Timer 8601
Oct 11, 2010 | TORK Variable Cycling Timer 8601
Aug 03, 2010 | TORK Digital Interval Timer Ssa100r-24
Jul 15, 2010 | TORK Digital Interval Timer Ssa100r-24
Nov 19, 2013 | TORK Variable Cycling Timer 8601
616 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: