Question about TORK Variable Cycling Timer 8601
Your power feed hot should connect to the black, the neutral to the white and the load should tie to the red. The neutral of the load will also connect to the white. The bare copper is the safety grounDING conductor and should tie to the grounds within you box and also to the grounding (green screw of the receptacles). I would NOT use this timer if you do NOT have grounds in the box or metal conduit to the boxes.
Posted on Oct 07, 2010
Hello Lee. The black wire is hot 110 volts. the red is hot 110 volts. the white is neutral and the bare copper is ground. IF you are only hooking up 4 outlets, only use the one hot wire [the black] do not use the red. Joe
Posted on Oct 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 19, 2014 | Woods In-Wall Digital 5-10-15-30-Minute...
May 30, 2012 | GE Hardware & Accessories
Dec 14, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Dec 02, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Nov 06, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Oct 30, 2010 | TORK Variable Cycling Timer 8601
Oct 11, 2010 | TORK Variable Cycling Timer 8601
Oct 06, 2010 | TORK Variable Cycling Timer 8601
Aug 03, 2010 | TORK Digital Interval Timer Ssa100r-24
Jul 15, 2010 | TORK Digital Interval Timer Ssa100r-24
Nov 19, 2013 | TORK Variable Cycling Timer 8601
43 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: