Question about Hayward H400idl2 400,000 Btu Low Nox Heater Natural Gas
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I dont know about your particular model. I do manage two Hayward 380,000 pool heaters that are natural gas fired and I have never had this problem you describe.
I also manage another dozen or so assorted other gas and propane devides. One propane device sooted so bad we had to discard it. It did this, according to the propane tech, because it couldn't breathe - there were louver type vents on the door that leads directly outside. He did, however, find a ruptured diaphram in the regulator and he replaced it. Hmmmmmm, couldn't breathe eh????
I'm not too surprised at the repair cost you cite. The exchanger is of course copper and there is the labor involved and lots of it. The age of your unit at this point is not relavent. What you do need to determine is why the unit sooted up like this. If you are gas fired, you know this is considered a clean fuel (compared to all others except electricity). What ever caused it must be repaired or you will be looking at another sooted up problem and repair ... and it will not be in three years, it could be next week.
I hope you find some value to my comments . Thanks for posting this question at FixYa.com
Positive comments welcome
Posted on Nov 02, 2009
The water is mixed on the back side of the heater and will exit the heater at 7-11 degres hotter than it came in. This will keep people from being scalded at pool side. So what you have sounds normal.
Posted on Apr 18, 2010
It means Ignition Failure. They heater went thru its startup cycle, and when the gas valve opened, the heater did not sense a flame. The whole routine begins again. After about 3 attempts at this, the heater will flash IF and then go into a lockout situation. This is a safety feature of this heater.
Posted on May 22, 2010
Tips for a great answer:
Aug 09, 2014 | Hayward Pool & Spa
May 24, 2014 | Hayward H-series Electronic Gas Pool...
May 08, 2014 | Hayward 250kbtu Ng Pool Heater - Inground
Mar 03, 2013 | Hayward H Series Pool & Spa Heater 400k...
Dec 30, 2010 | Hayward H Series Pool & Spa Heater 400k...
Oct 22, 2010 | Hayward H Series Pool & Spa Heater 400k...
May 22, 2010 | Hayward 250FDP Universal Series Propane...
May 05, 2010 | Hayward 250kbtu Ng Pool Heater - Inground
Jun 28, 2009 | Hayward H Series Pool & Spa Heater 400k...
Jun 26, 2009 | Hayward H Series Pool & Spa Heater 400k...
99 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: