Question about Hardware & Accessories
Switch has 2 wire > one of these wires is Hot and it connects to Timer black wire > the other wire goes to Load and connects to Timer red wire.
If you get these two wires reversed, timer will not run, so switch them. You know timer is running when dial on front of timer rotates with passing time. You can test for Hot wire by taking out switch, separate wires, turn on power, test each wire to bare ground, tester lights up with Hot wire.
Timer white wire goes Neutral. This wire is necessary to run clock inside timer. Locate Neutral wire inside box >> it is usually two or more white wires twisted together and pushed to back of box. If you do not have a Neutral wire, connect Timer white wire to bare ground wire ... until you can hire electrician to run additional wire to box.
Posted on Oct 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 22, 2013 | Intermatic Hardware & Accessories
Jan 03, 2013 | Woods 60 Minute Spring Wound Timer in...
May 27, 2012 | Solar Intermatic Single Pole Model Ej341c...
Aug 01, 2011 | Garden
Feb 26, 2011 | Leviton 6515M-W Timer Switch, 2-5-10-15...
Jan 23, 2011 | Broan-NuTone Fan,Bathroom Exhaust Broan...
Jan 22, 2011 | Solar Intermatic Single Pole Model Ej341c...
Nov 09, 2010 | Intermatic FF12HHC Energy Controls -...
Oct 03, 2010 | GE Electrical Supplies
402 people viewed this question
Usually answered in minutes!