Question about Heating & Cooling
Hi, follow what I say and it is very easy. The knob that says off, on, and pilot, is where you need to start. You don't want to turn it off now, as its been off for awhile now. Turn the knob slowly pushing down on it until you fill it go down. The knob will go down believe me. When this happens, keep holding it down as this is what starts the gas to the pilot which is back under the burner, under it. Just take a flash light and you can follow the aluminum tubing back and where it stops is where you light it with something long with a match in it or a small rolled up paper. Keep the knob down the whole time you are lighting it. When it lights, keep the knob pushed down for about another minute. Then slowly release the knob and the pilot should stay on. Once you have it on, turn the knob to on, not off. If you turn it the wrong way, it will go off and you will need to start over again. Once it stays on by itself, turn your thermostat up for heat and the burner will light and come on. Just remember that the pilot where you light it is where the tubing goes back under it, as the pilot gas goes through it. You will need a light. Look at the knob with a good light and it will tell you which way to turn it. In the pilot position, the knob will press down to let the pilot gas in, and you can reach back and light it. Then turn knob on. Pilot should stay light. Turn on thermostat and it will fire up. Let me know how it goes. You may have to try a couple of times.
A/C, & Heating Contractor
Posted on Oct 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 18, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
Nov 17, 2013 | Heating & Cooling
Sep 23, 2013 | Rheem Ruud Weather King Corsaire Rheem...
Jan 07, 2013 | Heating & Cooling
Jun 25, 2011 | Rheem 50 Gallon FVR NATGAS Water Heater...
Mar 11, 2011 | Heating & Cooling
Jan 27, 2011 | Heating & Cooling
Dec 28, 2009 | Heating & Cooling
Feb 18, 2009 | Water Heaters
Aug 21, 2017 | Heating & Cooling
912 people viewed this question
Usually answered in minutes!