Question about Broan-NuTone P66V Fan Control Switch
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: how do i hook up
Ok you only have two switches, so you would use one switch for your bathroom light, and the other for both the fan and the light, the light will come on when you turn the fan on.Connect the incoming black (hot) wire to both switches. Then connect the black wire to the switch you want for your light. Connect the other black to the second switch that goes to your fan and light. Connect the three white wires together (neutral) Connect all ground wires together, and leave a pigtail to connect to the ground terminal on the light switch. If you want separate switches for light in the fan and fan, you will need another conductor and a three gang switch.
Posted on Oct 17, 2010
Right now a single switch turns on both light and fan.
You want to put in a double switch to control light and fan separately.
But the problem is there is not a separate wire to each the light and fan.
You need a separate wire to each, but the circuit wasn't wired that way.
Usually when the circuit is wired for separate control, there is a red wire that also goes to ceiling box.
Unless you run another wire to the ceiling box, it won't be possible to control light and fan separately.
Electrician can do this pretty easily if there is attic space above bathroom.
Posted on Oct 17, 2010
I know wiring and we can solve this problem.
A better description of your wires in required.
Then 'add a comment' at bottom of page, and it e-mails me, and then I can hook up the wires for you.
The following 8 questions are key to solving the problem.
The heater-fan-light has how many wires?
Exactly what color are the fan wires?
How many cables enter the fan-light-heater box?
Does each cable have a black-and-white?
Are all these cables from the switches?
Are there other cables that enter the fan-light-heater box?
How many switches control the fan-light-heater device?
Is each switch a simple on-off switch or are there 3-way switches too (a switch at each end of a hall is example of a 3-way switch)
If you 'add a comment' I'll be here for next 3-4 hours
We'll get it done
Posted on Oct 28, 2010
I'm not sure what is going on without full and complete description of wiring and switches:
Add a comment with exact information for possible help.
Specs say 20 amp circuit is needed: so 20 amp circuit breaker + 12 gauge wire are required.
Heater uses 1500 watts, so it pulls a lot of power if same circuit breaker is used for several other rooms and a TV etc. Turn off everything else and see if problem persists.
Sell sheet for product says: Energy efficient lighting - uses one 27-watt (max.) high efficiency GU24 based fluorescent lamp.
Turn off power, and disconnect ground wire. Turn power back on and switch on the heater-lite and see if there is a fault to ground.
Use a different switch.
Posted on Aug 11, 2011
Tips for a great answer:
Apr 23, 2011 | Winix PlasmaWave 5000 Air Purifier
Jan 14, 2011 | Fantech Fans Exhaust Fan In-Line
Jul 13, 2017 | Air King AKDT60 White OnOffTimer Three...
Oct 28, 2010 | Broan-NuTone P66V Fan Control Switch
Oct 17, 2010 | Broan-NuTone Broan 68W White Decorator...
Oct 17, 2010 | Broan-NuTone Broan 68W Dual Rocker Switch
Aug 28, 2010 | American Standard Home
Jan 28, 2009 | Broan-NuTone N-LS100SE Exhaust Fan Exhaust...
Aug 10, 2008 | Dryers
Jan 04, 2008 | Fantech Fans Exhaust Fan In-Line
Dec 11, 2017 | Electrical Supplies
83 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: