Question about Goodman CKL24AR24 Air Conditioner
Outside fan motor runs backward
However, if it is the ORIGINAL motor, check the dual run capacitor for proper microferrad value. It may be that it is swelled up on top and that is a direct indication it is a fouled capacitor. If the top is not pregnant or swelled, and it still looks like the top of a soda pop can, you will need a microferrad meter.
Disconnect ALL power to the condensing unit. If in doubt, kill the power to home. Remove 1 wire from the capacitor, the brown one or the one that is marked "FAN" and set your meter to Mfd, measure with your leads the value between the COMMON and FAN terminals. They should be within 6% of the rating on the capacitor. There is no rule of thumb here, you must know the correct value and see if it is equal or within the 6%. If it is under the 6%, you will need to replace the DUAL RUN CAPACITOR. No question, because it is a dual run cap, it controls the Compressor also. Best to change the whole capacitor with that of equal value.
Posted on Aug 08, 2008
If the fan motor has been changed with a generic fan motor most have a set of wires that can be changed arround to reverse the direction that you need either clock or counter
Posted on May 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 18, 2014 | Dometic Rooftop RV Air Conditioner
on Jul 10, 2010 | Heating & Cooling
May 30, 2014 | Goodman CKL24AR24 Air Conditioner
Sep 18, 2012 | Carrier 38CKC036 Air Conditioner
Jul 17, 2012 | Goodman CLQ36AR49 Air Conditioner
Jun 22, 2012 | Heating & Cooling
May 02, 2012 | Heating & Cooling
Jul 09, 2009 | Heating & Cooling
May 07, 2008 | Nor-Lake Norlake Refrigeration 4' x 6'...
1,703 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: