Question about Heating & Cooling
Hi, there are a couple of things that will cause your air handler to ice up, some you may be able to take care of your self, and the last you will need to call out a service tech. First of all, you must have a clean filter at all times. 2nd, if the indoor coil has gotten dirty, this will cause decreased air flow across this coil and it will ice up very bad. Cleaning or I should say, getting to this coil to clean can be a job. You will have to bend the sheet metal panels, remove some screws, and work around the freon lines to get back to it enough to remove the sheet of dirt that is covering the coil. It will peel off like a sheet. When they get this way over the years, they will block the return air back through the coil, and it will ice up.Once it is cleaned, you may have to buy a roll of aluminum tape to seal the areas that didn't go back together very good. If your blower motor is not moving air very good, like it is ready to go out, moving slow, or making noise, this will do the same. The last thing that will cause this, is the unit has a small freon leak. If your air handler is gas, you can turn on the heat to melt the ice off faster, if not, turn just the fan on to melt the ice away. Once its gone and you have good air flow, turn the a/c back on and go to the outdoor unit. Place your hand above the fan guard to see if the air is good and warm to hot. Find the large copper line below and grab hold to make sure it is good and cold and is starting to condensate. The smaller line, discharge should be good and warm to hot. This will tell you the freon level is real close to being full, so your problem will more then likely be a dirty, plugged indoor coil. More then likely, this is your problem and would be something you could do your self to save you $$$$. I hope I have helped you on this and given you some direction to go on. I have done this for many years, and know the signs very well. Please don't forget to rate me as I know you will be kind. Please keep me posted on the outcome.
A/V, & Heating Contractor
Posted on Oct 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 30, 2017 | Heating & Cooling
Mar 11, 2015 | Heating & Cooling
Jul 06, 2011 | Heating & Cooling
May 15, 2017 | Heating & Cooling
Nov 26, 2009 | Heating & Cooling
Oct 27, 2009 | Heating & Cooling
Sep 16, 2009 | Heating & Cooling
213 people viewed this question
Usually answered in minutes!