Question about Ruud UBHC Air Conditioner
Im installing two ruud achiever airhandlers, one for a 2.5ton unit and the other for a 3ton unit, for the airhandlers I already have #6 wire run to the location of the unit can I use #6 to a disconnect and and then from the disconnect to the airhandler can I use #12 wire. Now for the breaker... Can I use 40amp in the main panel and 15amp in the disconnect?
Thank You, Hank.
Check the name plate amperage on the air handler. The air handler only has the blower motor as its main current draw. #12 wire is rated for 20 Amp service. If the amp draw by the unit supplied by the disconnect is under 15 amps it should be fine (but) once again check the name plate for ampacity rating.
Posted on May 27, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 04, 2016 | Ruud Heating & Cooling
Jul 18, 2011 | Ruud Handler Air Conditioner
Mar 10, 2011 | Ruud Heating & Cooling
Aug 24, 2010 | Ruud Matching Split Air Conditioner
Aug 18, 2010 | Ruud Heating & Cooling
Jul 12, 2009 | Ruud UBHC Air Conditioner
Feb 21, 2009 | Ruud UBHC Air Conditioner
Aug 18, 2008 | Ruud UBHC Air Conditioner
Nov 24, 2007 | Ruud UBHC Air Conditioner
143 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: