Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
you may have a factory defective unit that is not turning off the anti-frost heating coil (I have assumed yours contains this item based on your problem description). I would trade it in for a new unit, again assuming you have a warranty or the store offers a good in-store return policy. If this plan bombs, then open the unit and find the heating coil near the cool side of the radiator fins. then disconnect the power wires to the heater and prevent electrical short to wires with quality electrical tape.
Posted on Jul 07, 2007
Check at the compressor terminals between the Red and the terminal for the overload protector to see if you are getting power to the compressor on startup.
Posted on Jul 24, 2008
SOURCE: blows room temperature air
Welcome to fixya.
I'm Huuum and happy to assist you
The air conditioning
unit works, but does
not cool the room
• window open
• there are heat sources in the room (burner,
• the exhaust hose is detached
• air filters clogged
• Inadequate size of the room (too large)
• close the window
• eliminate the heat source
• connect the exhaust hose
• clean or replace the filters
If all this dose not remedy the problem then you need to see service!
Please remember to leave a rating before you go!
Posted on Sep 29, 2008
Check each screw on your compressor to ground (compressor case). Should be very high resistance Then check the resistance across your teminals on the compressor to be sure it is not shorted. Then check the wiring to your capacitor (The big one). I ran across this just last week. The mechanic didnt have the capicator wired correctly. If it is brand new it will have a wiring schematic somewhere on it.
Dont leave the compressor on very long, but turn it on long enough to get a voltage reading across the terminals. I assume it should be 240 volts. If you have check all of this, they make a jump start gadget to start a stuck compressor. They sell it just about everywhere. Let me know how this comes out..
Posted on Sep 30, 2008
need to add refrigerant
need to check wheather the ampere is the same on the name plate
check the room temp. setting
check the setting of the timer
Posted on Jan 26, 2009
Tips for a great answer:
Jul 02, 2015 | Cfm Daikin R410a Split System Air...
Sep 10, 2014 | Heating & Cooling
Nov 06, 2013 | Dometic Rooftop RV Air Conditioner
Oct 21, 2011 | GE Quiet-Aire Ductless Mini Split System...
Aug 25, 2009 | LG LS092CE Split System Air Conditioner
Feb 16, 2009 | Cfm Daikin R410a Split System Air...
Jul 13, 2008 | DeLonghi Pinguino PACL90 Portable Air...
Jun 07, 2008 | GE Zoneline AZ38H12DAD Split System Air...
423 people viewed this question
Usually answered in minutes!