Question about Sanyo Split System Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If anything, it appears undercharged. Purging is not recommended. @90 degrees the high side corresponding pressure is 168.4 and Low side coresponding numbers re70psi/68degrees. With all due respect to the tech I think . If your room temp is 80, the corresponding high aide pressure is 143.6 , Low side 85 psi Yup, undercharged. Now do me a favor and don't start any "but he said" wars going. If anything, Just call him back and tell him something is still not right. Ask him to bring you a pocket rergerence for temp/pressure relationships. The numbers I gave you are for R-22 which is commonly used in residential applications. Well, good luck and keep your cool. IDon't purge. R-22 is very expensive asis everything else. You may want to dispute anny additional service call charges. Good Luck
Posted on Aug 22, 2009
The condensate drain line was not properly installed. Make them pull the wall unit and correct the problem.
Be persistant until you are satisfied they have the problem corrected. Do not pay any additional money. If they do not correct the problem then report them online to the state board of heating and air. Fill out their requested complaint form and follow thru with a second complaint if you do not get total satisfaction from the contractor that installed the unit.
Hope this helps.
Posted on Sep 23, 2011
Tips for a great answer:
Apr 17, 2014 | Sanyo Split System Air Conditioner
Mar 30, 2014 | Sanyo Split System Air Conditioner
Jan 05, 2012 | Sanyo Split System Air Conditioner
Mar 11, 2011 | One For All URC-3021 Remote Control
Jul 20, 2010 | Sanyo Split System Air Conditioner
Nov 26, 2009 | Sanyo Split System Air Conditioner
Apr 23, 2009 | Sanyo 24KS72 Split System Air Conditioner
63 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: