Question about RELIANCE ELECTRIC WATER HEATER
This is not an "overflow". It is a Temperature/pressure relief valve. Sometimes they leak with age or build up solids in valve preventing them from closing completely. This is the single most important safety device on your water heater. If one of the thermostats is malfunctioning, the TPR valve will relieve. If the pressure rises too high, it will also relieve. You can replace the valve, but be sure it is the same temperature and pressure rating. You will need to turn the water off and drain some of the water prior to removing the valve. Don't forget to reinstall the down pipe that directs floor to floor or drain. If a new one leaks also, suspect your temperature control. Water heaters can be bombs if the safeties are not working properly
Posted on Oct 02, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 30, 2017 | Water Water Heaters
Mar 23, 2013 | Water Heaters
Jul 29, 2012 | Water Heaters
Jul 14, 2011 | Rheem 81VP6S/430126 Water Heater
Jul 03, 2011 | Rheem 40 GAL ELEC TALL Water Heater 6YR SC...
May 25, 2010 | Noritz 6.3 Gallon Residential Tankless...
Nov 08, 2009 | RTO Santon® Tankless Hot Water Heater -...
Oct 20, 2009 | Water Heaters
Oct 15, 2009 | Water Heaters
309 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: