Question about Amana Heating & Cooling
Goodman split type system, model MSG12CRN1W Want to know how the refrigerant tubing should be connected, I believe it may have been installed incorrectly
Hi, this is very easy to find out. The out door unit has 2- copper lines coming out of it. A small one on the unit, 3/8" and a large one either a 3/4" or 7/8" depending on the size.2- rolls of copper called the line set are silver brazed into the fittings coming out of the outdoor unit of the same size and uncoiled and ran to the indoor evaporator coil. Again, one is brazed into the smaller open fitting, 3/8" and the other into the larger of the two. There is only one way to install these as the open fittings are made for you to put your lines into at the factory and silver braze them. They could have cut a line and did there own design, but that would be wrong. What kind of problems are you having? I have seen installers add to many joints to connect to and they would be in the way of the panels going on right, but its pretty much cut and dry, a larger suction line at each end, and a smaller liquid/discharge line on both ends. Please let me know the problem?
A/C, & Heating Contractor
Posted on Oct 01, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 05, 2015 | Goodman Heating & Cooling
Oct 07, 2014 | Goodman Manufacturing Goodman R410A 13...
Jul 24, 2014 | Goodman Manufacturing Goodman MSG18CWN1W...
Jul 10, 2013 | Goodman Manufacturing MSG12CRN1N -...
Aug 08, 2010 | Goodman CPLE24-1 Air Conditioner
Mar 19, 2010 | Goodman CKL42AR42 Air Conditioner
Feb 23, 2009 | Cfm Daikin R410a Split System Air...
Feb 16, 2009 | Goodman PHKJ048-1 Air Conditioner
Dec 27, 2007 | Goodman GDS80904BNA Open Flame Heater
263 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: