Question about Heating & Cooling
i think you did wrong connection with compressor please make sure first your connection is correct then install your compressor unit make vacuum in unit and then try to fill freon also use over load protectors in compressor for security .correct connection are giving you blow :
C : connect here wire which one is coming from main supply/thermostat /overload protectors
R :connect here wire which one is coming from capacitor ( C terminal).
S : connect here wire which one coming from H terminal of capacitor if capaciter/if capacitor is no mark then one wire i mean no require from H OR C terminal .
hope answer the question
Posted on Oct 01, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 17, 2017 | Refrigerators
Jan 29, 2015 | LG Heating & Cooling
May 29, 2011 | Dometic Rooftop RV Air Conditioner
Jan 11, 2011 | Amana Heating & Cooling
Dec 28, 2010 | LG LWHD1500ER Wall/Window Air Conditioner
Apr 19, 2010 | Hitachi EC12 Portable Electric 2hp Air...
Sep 06, 2009 | Refrigerators
Aug 15, 2009 | Heating & Cooling
Mar 31, 2009 | LG Heating & Cooling
Aug 06, 2008 | Frigidaire FAA065M7A Air Conditioner
Dec 15, 2017 | Mitsubishi Heating & Cooling
52 people viewed this question
Usually answered in minutes!