Question about Leviton Electrical Supplies
Review old switches:
Two old switches > each has 2 wires
Old switch 1 > Red and White
Old switch 2 > Black and White
The same white wire connects to both switches, so effectively they count as 1 wire
This means you have 3 wires ... 1 White, 1 Red, 1 Black
Each switch controls a separate load (light, fan, motor)
New Leviton double-rocker switch:
-Leviton has 2 Brass-colored screws on one side, and these screws are connected together by a brass plate >> your Hot wire will connect to brass screw
-Leviton has 2 Silver-colored screws on other side, and neither of these screws are connected in any way >> the wires going to each load will connect on a different screw on this side of switch.
Hot wire: Each box in your house has exactly 1 hot wire that is connected back to breaker box. This is true for all boxes (excluding boxes that have a 3-way & 4-way switches).
We need to identify Hot wire.
-By code the Hot wire is black for identification purposes ... but your box sounds like maybe the Hot wire is White.
-If your Hot wire is white, that is NOT an immediate safety issue ... it will not cause a fire or malfunction ... it is a code violation ... because code requires things be uniform so next electrician knows what previous guy did. So some day, electrician working outside grabs wrong color wire, and wow. I say this so you know.
Identify Hot wire:
-Pull 3 wires up so they can be tested
-Turn on power
-Use ordinary tester, or old lamp with plug cut off and wires stripped back
-Tape tester lead to sticks so hands are away from voltage
-Power is on. Don't stand in water or touch metal pipes, and you're fine.
-You have 3 wires in box + ground wire
-Test all 3 wires to bare ground wire >> when tester lights up, that is Hot wire ... testing is complete
Connect wires to Leviton double-rocker:
-Power is OFF.
-You have 3 wires - 1 White, 1 Black, 1 Red >> one is Hot wire, the other two wires go to load
-Hot wire connects to Brass-colored screws on new Leviton.
-Brass colored screws are connected together by a brass plate so the Hot does not need to connect to both brass screws.
-The other two wires connect to Silver screws on other side of new Leviton switch
-One wire goes to each silver screw
-Connect bare ground wire to green screw.
-Push wires back into box. Use eraser end of pencil if needed.
-Make sure ground wire is back and away from screws on switch
Posted on Sep 30, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 30, 2014 | Leviton 5634 Dual 1 Pole Switch Decora...
May 16, 2014 | Leviton R03-5634-A Two Single-pole...
May 14, 2014 | Leviton 5634 Dual 1 Pole Switch Decora...
Feb 10, 2013 | Electrical Supplies
Jun 09, 2011 | Leviton 5634 Dual 1 Pole Switch Decora...
Feb 24, 2011 | Leviton 5634 Dual 1 Pole Switch Decora...
Dec 26, 2010 | Leviton 6230M Decora Four Preset...
Feb 22, 2010 | Leviton 003-1755-W Three Rocker Switches
Jan 20, 2010 | Leviton COMBINATION SINGLE POLE TOGGLE...
715 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: