Question about Heating & Cooling
Try the connector at the top of the boiler where the fan and the pressure sensor switch connect.This connector can corrode causing the power to not get to the fan. I looks like an ordinary terminal block but actually is a pin connector. Pull the connector apart, clean the pins and the inside of the sockets with fine emery paper, carefully prise the two halves of each pin apart and reconnect the connector. Be careful with the last step otherwise you can break the pins!! To get access to the connector remove the outer casing of the boiler and then the inner front plate - you will see the fan and the offending connector at the very top.
Posted on May 03, 2009
What do you mean "moved the position" of the boiler?
Posted on May 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 12, 2014 | Water Heaters
Nov 20, 2013 | Computers & Internet
Dec 20, 2012 | Water Heaters
Nov 04, 2011 | Combi Centre DX - Mango
Jan 14, 2011 | Heating & Cooling
Dec 19, 2009 | Water Heaters
Oct 03, 2009 | Water Heaters
Sep 21, 2009 | Heating & Cooling
Nov 30, 2008 | Bosch Water Heaters
159 people viewed this question
Usually answered in minutes!