Question about APC Smart-UPS 2200XL (APCSMART2200XL) UPS System
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: APC Smart-UPS 1500VA
yeppers...those APC units sometimes kick the monitoring software. sometimes you need to unhook the connection cables(like a reset) so that the firmware can 'unlock' which can cause that christmas tree effect on the panel lights.
Posted on Feb 06, 2008
A UPS 500 uses two smartcell batteries. As for the APC Smart UPS, there are different models, but most UPS's will generally use two batteries.
Posted on Jun 23, 2009
Posted on Feb 19, 2010
SOURCE: We have a APC Smart
The light pattern indicates the batteries need to be replaced. The typical life of UPS batteries is 2.5 years, after this time the cells will not hold the proper charge. When your power when off last night the UPS would have tried to switch to battery power but it most likely failed after just a few minutes as the batteries shorted. The UPS has a protection circuit that prevents it from starting up properly with dead batteries so you get the flashing lights and the unit shuts off. The batteries are available in most cities from car battery dealers, not like Wal-mart but battery only dealers, just look in the yellow pages for batteries. You can take the old batteries out of the unit by removing the front panel and unscrewing the metal plate just behind the front cover. The old batteries are connected with a wiring harness that plugs in. Just bring the old batteries to the dealer so they can get you the correct replacement part. The new ones should be less than $100 so it is well worth the price compared to a new unit.
I hope this helps, if so please rate our solution.
Posted on Feb 04, 2011
Tips for a great answer:
Apr 19, 2014 | APC Smart-UPS 2200XL (APCSMART2200XL) UPS...
Feb 07, 2013 | APC Smart-UPS 2200XL (APCSMART2200XL) UPS...
Feb 04, 2011 | APC Smart-UPS 2200XL (APCSMART2200XL) UPS...
Nov 08, 2010 | APC Smart-UPS 2200XL (APCSMART2200XL) UPS...
Aug 20, 2010 | NEC APC Smart-UPS 1400 (050-01803-000) UPS...
Jun 14, 2010 | APC Smart-UPS 1500VA Shipboard...
Feb 19, 2010 | Enterasys APC Smart-UPS 2200 XL...
Apr 25, 2009 | APC Smart-UPS 1000VA UPS System
Apr 18, 2009 | APC Smart-UPS 1000VA UPS System
Aug 18, 2017 | APC Smart-UPS 2200XL (APCSMART2200XL) UPS...
424 people viewed this question
Usually answered in minutes!