Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If you pull the unit out of the case it should have a wireing diagram in a envelope near the compressor
Posted on Jul 17, 2009
Hi, dealing with these ductless split systems on a daily basis, I can say you have checked some of the things I would have wanted you to check, which is good on you're part.Blowing Room Temp. air in both heating and cooling indicate that the compressor is not running even though the outdoor condenser fan is on.There are several things that could cause this. You have a compressor run capacitor that starts the compressor, but I am thinking on you're unit, it has a dual capacitor that runs the compressor and fan together. Fan is on, so I will rule this out.These units are notorious for leaking freon as the Liquid line and suction lines are not brazed, they are put together with connectors that tend to leak over time. If it is low enough on Refrigerant gas, the compressor will shut off and stay off on low pressure. This unit has a low pressure switch that has normally closed contacts, that opens and stops the compressor from any damage which in turn, you will have no cooling or heating.Do this for me, turn the unit on in cooling, lower T-stat way down so outdoor unit comes on. Go to the out door unit and where the elect. wiring and lines go into unit you will see to copper lines. The largest of the 2 lines is the low or suction line.Wrap you're hand around it and it should be nice and cold. If it is warm, just touch the smaller line, it should be rather warmer, almost hot.If both lines are of normal temp. you are either out of freon or the compressor isn't running.You can remove panel to get to it and put your hand on it to see if it is on. If the lines were of normal temp. and the compressor is not on, more than likely you have lost the charge.Look it over, the wiring to see if you see anything burned or connections burned off and so on. You can check the 3 wires going into the compressor by turning off the power at breaker and removing the cap covering wires just to make sure these wires are intact. sometimes one will get hot from power and burn off. If you see this problem, it would be something you could fix.If all looks good, go back to the copper lines and being this is a Heat-Pump, you should have 3 fittings where we install our gauges to check and fill systems with freon. Look for one that is on the unit itself and remove the plastic cap.Don't be alarmed if you do as nothing will come out.If you look inside the valve, and you see a Schrader core, you can depress it with a nail or something small, just enough to see if it has a lot of pressure in it.If very little or none, the system is out of freon. You will have to call a tech out to find leak and evacuate and re-charge system.I wanted to give you many things to check so you and I would know what the problem is, a process of elimination. If you have a lot of pressure, then more then likely you have a faulty compressor. If you feel that you would rather not check the electrical or depress the Schrader, I fully understand.You can at least check the temp. of the lines and listen to see if the compressor is running, and if it is with warm lines it is still low on freon.Please keep me informed, and again the long explanation was for you to understand more about you're system operation. Sincerely, and best of luck,
Posted on Nov 23, 2009
Just had the Amani service guy out. Had the same problem. It was the capacitor. Took about 15 mins to fix. The machine turns off to protect itself because it knows something's wrong
Posted on Jan 06, 2010
SOURCE: We have a spit system
Leaking water from indoor is a common problem. Please check the following:
1. Cooling coil and air filter blocked-Clean it. 2. Drain pan and hos dust blocked-Clean it. 3. Non insulated pipelines-Insulate properly. 4.Less rpm of blower motor.-Replace capacitor.
Posted on Jan 01, 2011
Tips for a great answer:
May 15, 2017 | Heating & Cooling
Jan 07, 2016 | Sanyo 24KS72 Split System Air Conditioner
Jan 22, 2011 | Heating & Cooling
Dec 16, 2010 | Heating & Cooling
Aug 18, 2010 | Soleus KFR-18GW Split System Air...
Oct 17, 2009 | Mitsubishi Mr. Slim MXZ30TN Air...
Jul 17, 2009 | Frigidaire FAA065M7A Air Conditioner
Feb 20, 2009 | Soleus KFR-18GW Split System Air...
Jan 05, 2009 | Heating & Cooling
207 people viewed this question
Usually answered in minutes!