Question about Noritz N-069M-DV, N-084M, and N-084M-DV Pipe Cover
F12 occurs on a multi-system or quick connect. It means one of the units on the system suffered a flame loss. More specifically, it means the flame rod stopped detecting flame on the burner. The most typical causes are as follows:
1) insufficient BTUS (low gas pressure)
2) leaking heat exchanger
3) clog in the manifold, burner, or heat exchanger
4) stuck flue damper or improperly sized venting
5) dirty flame rod
6) damaged circuit board or gas valve
Posted on Oct 19, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 12, 2014 | Noritz Commerical Tankless Water Heater...
Jul 14, 2012 | Water Heaters
Mar 10, 2011 | Noritz 6.3 Gallon Residential Tankless...
Jul 31, 2010 | Noritz 6.3 Gallon Residential Tankless...
Feb 24, 2010 | Noritz 6.3 Gallon Residential Tankless...
Feb 18, 2010 | Noritz 6.3 Gallon Residential Tankless...
Nov 01, 2009 | Noritz 6.9 Gallon Residential Direct Vent...
Aug 06, 2009 | Noritz N-069M-DV, N-084M, and N-084M-DV...
Jan 04, 2009 | Noritz 6.9 Gallon Residential Direct Vent...
294 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: