Question about Goodman Heating & Cooling
Your system could have lost its refrigerant charge through a leak. Check for visual signs of oil at any soldered joints. This would indicate a leak at a point where some oil is visible. Also check for frost on the big line that returns to the outside unit. If frost is present set you air circulation fan to the on position and turn the cooling to off. Allow the air to circulate for about an hour. Then return the system to the cooling mode. Operate the system when cooling with the fan in the on position in this case.
Posted on May 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 20, 2014 | Goodman CKL42AR42 Air Conditioner
Oct 25, 2013 | Goodman Manufacturing...
Sep 07, 2010 | Goodman CLJ30AR32 Air Conditioner
Jul 15, 2010 | Goodman CKL60AR60 Air Conditioner
Jun 24, 2010 | Goodman CLJ30AR32 Air Conditioner
Aug 11, 2009 | Heating & Cooling
Feb 13, 2009 | Goodman Heating & Cooling
Jun 17, 2008 | Goodman Heating & Cooling
67 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: