Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There is probably more than one limit switch. I'll have to get a wiring diagram of this unit. See if you can follow the wires from the wires from the limit switch and see if they go to another limit switch. Also you can put a jumper wire on the red wire and white wire on the unit outside and see if ti comes on.
Posted on Nov 03, 2009
There should be a reset button in the upper chamer next to the fan motor. In the middle ,push in on the center red button to reset it, this tripps because it says I,m not gettig enough air flow due to a plugged or dirty fliter located on the front cover or door.
Posted on Dec 18, 2009
Tips for a great answer:
May 10, 2017 | Intertherm Heating & Cooling
Sep 20, 2015 | Heating & Cooling
Apr 10, 2015 | Intertherm Heating & Cooling
Feb 16, 2015 | Intertherm Heating & Cooling
May 15, 2014 | Intertherm P3RA-048K Air Conditioner
Feb 07, 2014 | Intertherm Heating & Cooling
Nov 05, 2013 | Intertherm P3RA-048K Air Conditioner
Oct 26, 2010 | Intertherm Heating & Cooling
Jan 02, 2010 | Heating & Cooling
32 people viewed this question
Usually answered in minutes!