Question about Bryant Heating & Cooling
Have someone check the pressures & temperatures in the refrigeration system.
Posted on Dec 06, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If you can hear the A/C compressor start and run then your system has lost it's charge of refrigerant. If the compressor does not start and run it could be a control problem.
Posted on May 17, 2008
When the unit is running, go outside and put your hand near the condenser fins, this air that comes out should be slightly warmer than the ambient temp. If it is not you will need to take the unit out of the window and out of its outer case and clean the condenser fins from the inside, this is no easy task as it is very hard to reach. You will want to get a small (toothbrushed sized) brass bristled brush with a long handle. Make sure the evaporator coil (in the front) recieves the same attention and wash the mesh filter that goes in front of the evaporator. Re- assemble and enjoy the cold air.
Posted on Jun 07, 2009
If the a/c fails to continue to blow cold there could be a few problems you can look for. First once you activate the system check to see if the compressor kicks in. You will hear the compressor humming . Once the a/c quits cooling go and see if the compressor is still running. If its not running its probibly gone into thermal overload (compressor overheated). If that is the case then you need to check to see if the coils are icing up if they are icing up then the problem is with 1) air flow restriction filter dirty, coils dirty simple repairs there replace filter, clean evaporator coil with a coil cleaner that can be purchased at a home repair store cleaning the condensor coil the same. 2) system is low on freon in which case the system will need to be recharged. Also, If you have a digital thermostat replace the batteries that may also be of some help. Good Luck on repairs
Posted on Aug 31, 2009
it is likely low on coolant or as some say "freon" that or the indoor fan motor has not run properly. let it thaw completely by shutting it off and just turning on your fan switch from auto to the on positon. if you begin to feel air flow eventually you need coolant added b/c you probably have a leak from the system being old
Posted on Sep 13, 2009
Tips for a great answer:
Sep 25, 2012 | Bryant Heating & Cooling
Sep 07, 2012 | tranexp.com Computers & Internet
Jul 22, 2011 | Bryant 463AAC005BA Air Conditioner
May 09, 2011 | Heating & Cooling
Sep 17, 2010 | 2003 GMC Yukon XL
Aug 01, 2010 | Bryant 463AAC008BA Air Conditioner
Jun 13, 2009 | 2005 Chevrolet Colorado
Mar 22, 2009 | 2004 Dodge Intrepid
69 people viewed this question
Usually answered in minutes!