Question about Honeywell Air Conditioners
SOURCE: I want to adjust the
To enter the adjustment mode, press the UP, DOWN, and I buttons simultaneously for three seconds. Press the I button until the feature requiring adjustment is displayed:
HL High Limit.
LL Low Limit.
Ldf Low Limit differential.
Then press the UP and/or DOWN buttons to move the set point to
the desired value. After 60 seconds without any button inputs, the
control will automatically return to the READ mode.
(copied from honeywell's instructions)
to clarify the differential is cut in minus the cut out.
Hope i can be some help to you.
Posted on Apr 21, 2008
SOURCE: have an oil fired boiler
These boilers usually have multiple controls. The control that would take it out of the circuit at 210 degrees is a safety.
You should definitely have a professional take a look at this unit before you continue using it.
Posted on Sep 18, 2008
I would say high if you need cooling. If the tempature is cool enough for you then set it to low.If you are hot and need more cooling then high.
Posted on Apr 07, 2009
SOURCE: HI IAM A ELECTRICIAN WORKING
I would suspect a water circulation problem, most likely air in the system, if the water can't flow it will overheat.
If the problem persists after bleeding check to make sure the pump is running
Posted on May 06, 2010
SOURCE: My L4103 aquastat is set
on the left side of the dial will be a little metal arrow that will not move when the dial moves, this is the set point. set the temp. you want at this point.
Posted on Dec 17, 2010
Tips for a great answer:
Jan 25, 2013 | Air Conditioners
Mar 16, 2011 | Air Conditioners
Feb 19, 2011 | Air Conditioners
Dec 17, 2010 | Honeywell Air Conditioners
Sep 30, 2010 | Air Conditioners
May 06, 2010 | Air Conditioners
Apr 21, 2009 | Air Conditioners
Apr 05, 2009 | Honeywell Air Conditioners
Jun 08, 2008 | Honeywell Air Conditioners
Apr 21, 2008 | Air Conditioners
546 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: