- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
COLEMAN R.V. PRODUCTS
GO TO rvcomfort.com
Click on RVP (RV PRODUCTS)
Click on type of AC, if you can’t find the information you want there,
then click on contact us on the Green Bar.
You can get Service Support or Email address and Phone numbers.
It probably has a clogged condensate drain. Take off the cover on top the RV and check hoses or tubes leaving unit for debris or lint. Often this water is used to help cool the condenser so look for leaves pine needles etc in the pan. There may be a cover you can remove on the evaporator section that will allow you to clean the collection pan and hose or trough. Is it possible the RV is far enough out of level that the condensate can't "run uphill"? Always power off while working on this unit unless you are electric savvy. Good luck!
I don't think you need a new one just a good cleaning and service. The unit has a liquid high temperature line near the compressor with a fan blowing outside air across it this coil gets clogged over time with air-borne dirt and pollen and leaves and such and must be cleaned regularly or the unit will be unable to remove the heat from the coil and during the peak demand (3pm) the circuits that protect the compressor and the trailer wiring from being overloaded and burning or melting will trip. From what you have described it sounds like the RV is working as it should with a condenser coil that needs to be cleaned. GL and happy camping! P.S. I've only serviced the occasional RV unit but in those cases I laid a piece of plywood on top of the Rv for work platform removed the retaining screws from the top cover and used a spray bottle with a good heavy foaming cleaner a shop-vac and a brush to get the job done.
the fan motor bearings need lub....the shaft has a tiny access hole to put some oil into. because the fan shaft is slowing down, it is putting more strain on the voltage current, and eventually the internal breaker shuts down the ac........plus your condenser is not getting enough air accross it, compressor heats up, and it too will shut the unit down......older units have to be oiled every year, and eventually it too will fail, and a new blower motor assembly is needed or replace the ac unit.....blower motor units are around $130....now you install it or pay to have it done at around another $150 labor,,,,,try yourself, if it fails then call the tech........let me know ..ray..firstname.lastname@example.org