Question about Goodman CKL60AR60 Air Conditioner
All the above and it might need a bigger return on your a/c vary how big is your unit approx 16 min to 20 in. return air flow
Posted on Aug 25, 2008
Show me a picture of acoil
Posted on Jul 31, 2008
Icing up is either 1--or 2 things, low-airflow across the indoor coils, or low on freon, bottomline! firstname.lastname@example.org
Posted on Jun 09, 2008
Four things cause icing up:
( 1 ) Is your filter clean? dirty filter blocks air flow causing iceing up. replace filter
( 2 ) Do you hear the Indoor fan running? If the fans not running the unit ices up. Check Capacitor to fan if good.
Bad fan motor... replace fan motor and cap. If both good
( 3 ) Check Air Handler evap coil if dirty and or clogged, restricts air flow causing unit to ice up. Use toilet brush to clean.
This is always a big possibility if you have pets.
( 4 ) If the above are not present then you are low on refrigerant.
Low refrigerant will cause icing up because the gas does not flash properly. This will require a service tech.
refrigerant leaks can be as simple as a loose cap on the king valve, leaking schrader core, to coil leak.
Have the service tech show you the leak. If it is in a copper line it can be fixed. If the system is over 10 years old limit the amount you want to spend. 10 years is the standard life expectantcy anymore. Good luck
Posted on May 20, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 14, 2014 | Goodman CLQ36AR49 Air Conditioner
Jun 17, 2013 | Heating & Cooling
Jun 08, 2012 | Goodman Heating & Cooling
Aug 19, 2011 | Goodman CLQ36AR49 Air Conditioner
Jul 11, 2011 | Goodman CKL36AR36 Air Conditioner
Dec 27, 2010 | Heating & Cooling
Aug 15, 2009 | Heating & Cooling
May 29, 2009 | Goodman CLJ30AR32 Air Conditioner
May 16, 2009 | Goodman Heating & Cooling
Mar 09, 2009 | Goodman CPLE24-1 Air Conditioner
609 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: