Question about Ruud UAKA037 Air Conditioner
What steps might i take to check on the blower fan indoors to my unit.
It seems to have stopped running.
Its a rheem air conditioner..i can't find it listed
Have someone turn the thermostat to fan on. stand by the air handler. listen for a click. There is a fan relay or a stack switch both click when power is sent to them .
If you do hear a click that is good. should be good part.
No click means the relay or stack switch may be bad.
also look at the capicator. it's a little silver oblong or round component with 2 wires to treminals on the end. These wires are usually brown. The top of the capicator where the wires attach should be flat. if it is a little rounded the cap is bad.
If the cap is good and the relay is good.
SECURE POWER to the Air Handler. At the breakers
touch the side of the motor. BE CAREFUL it could burn.
touch lightly... if real hot motor is more than likely bad.
The Motor has the specks on the side of it. and can be read after the motor is removed.
Two screws must be removed to remove motor.
If you must disconnect wires to remove. write down where they connect and there colors Before disconnecting.
Posted on May 20, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 19, 2014 | Goodman CKL36AR36 Air Conditioner
Feb 05, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Feb 14, 2013 | Heating & Cooling
Aug 21, 2011 | Ruud Heating & Cooling
Jul 11, 2011 | Ruud Heating & Cooling
Jun 03, 2010 | Heating & Cooling
Mar 18, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Aug 11, 2008 | LG LS-L1210CL Mini Split Air Conditioner
Dec 10, 2007 | Heating & Cooling
91 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: