Question about Traulsen Reach in Freezer - G12010
I have a 6 year old Traulsen freezer, model G12010. The freezer will cool to 59F degrees and then a loud high pitch sound followed with a sound of running water coming from what I think is the compressor. The temperature then goes up to 70F degree. The fan is working well (1 year old) and the coils are clean.
Question: Is it worth calling for service or should I trash it?
Posted on Mar 25, 2017
It sounds to me like the internal relief valve is lifting due to discharge pressure being to high such as it a system that is over charged with refrigerant. Have the system tested for pressures on high and low sides. If someone has serviced this unit recently there may be to much of a charge in the system. Also check the name place for the proper refrigerant and charge .
Posted on May 19, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 26, 2013 | Traulsen Freezers
Jul 31, 2010 | Traulsen G20010 Commercial Refrigerator
Jun 05, 2010 | Traulsen UR48DT-6 Refrigerator/Freezer -...
Aug 20, 2009 | Frigidaire 20.6 cu. ft. Upright Freezer...
Jan 30, 2009 | Kenmore 64823 Top Freezer Refrigerator
Jul 24, 2017 | Traulsen Reach in Freezer - G12010
Dec 31, 2007 | Refrigerators
537 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: