Question about Heating & Cooling
Check electrical breakers turn them off then back on. To reset them.
How long has it not worked?
Does the fan come on if you put the fan in the ON position on the t-stat.?
Is this a heat pump? If so does any lights show up on the t-stat if you put the t-stat in emergency heat?
Give me more information.
Help me out so I can help you.
Posted on May 20, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a Amana air
This sounds like your condenser contactor, contacts are stuck. They weld together if an ant or other debree get between the contacts. Turn off the electric breaker to the outdoor unit as if the outdoor unit runs without the indoor unit running you may damage your outdoor unit compressor.
I would suggest you call a service company. The part should run retail @ 30 to 40 dollars then the service call charge. This repair should take less than 1/2 hour.
Posted on Oct 18, 2008
The blower motor kicks on when there has been a 24 volt control failure.
This usually means that a limit switch has tripped.
Most likely that would be a high temp limit switch or a rollout switch.
First, make sure the filters are clean. and the evap coil is clean. If eaither are dirty/clogged, it will partially block airflow, causing the furnace to overheat, causing the high temp limit to trip.
A rollout switch typically trips for three reasons.
1 flame rollout into the burner compartment due to poor airflow.
2 overheating af teh metal plate the rollout is mounted to, due to dirty, old, rusted components.
3 a bad limit switch.
If your unit has an LED light, count the flashes and it will hepl popint out the problem.
(locate the wiring diagram/flash code list, and correspond the flash count, with the code.)
First, check filters.
Posted on Jan 14, 2009
This is a condenser fan and as long as the A/c unit is in cool mode, this fan will run. The only time it should shut off is when temperature setting is satified and the unit shuts off.
Posted on Jun 05, 2009
Tips for a great answer:
Aug 22, 2013 | Ruud Central System Air Conditioner
Feb 08, 2011 | Heating & Cooling
Apr 06, 2010 | Heating & Cooling
Jun 21, 2009 | Jackson 25 in. TempStar HH70 Free-standing...
Feb 11, 2009 | Ruud Central System Air Conditioner
Jun 12, 2008 | Honeywell Electronic Programmable...
Jan 18, 2006 | Haier Energy Star ESA3183 Air Conditioner
Apr 24, 2018 | Heating & Cooling
695 people viewed this question
Usually answered in minutes!