Question about AmcorAire UCHW-H12AF2 Split System Air Conditioner
The cooling fan never shuts off in the cool mode. Worked perfect last summer. Works perfect in the heat mode. The heat pump shuts off and cycles as normal but the room temp isn't maintained in the cool mode. just gets colder. I'm thinking the relay must be stuck or maybe a bad temp sensor.
Unit too large for area
Posted on Jul 03, 2011
Simple Question: Did you check to see if the fan switch on the
t-stat is in ON or AUTO? If ON the fan runs nonstop. If in auto the fan cycles with the outdoor unit.
next does the fan shut off if you turn the t-stat to off?
A stuck relay should keep the fan running all the time.
Sometimes if the relay is stuck you can whack the side of the Air Handler and the connection will break.
Sometimes instead of a relay there is a stack switch.
It's a little black stack of 3 disks this is a bi-metal switch.
they do get stuck more often than relays.
The fan relay may be on a electronic board. I don't know for sure without seeing your unit.
Good Luck Phil
Posted on May 20, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 22, 2014 | Carrier 3 Ton Infinity Puron A/c outside...
May 14, 2013 | Honeywell Rth2310b 5-2 Day Programmable...
Oct 28, 2012 | Honeywell Programmable Thermostat Heater
Sep 28, 2011 | Goodman GMS90703BXA Heater
Nov 05, 2010 | Goodman PHKJ048-1 Air Conditioner
Dec 06, 2009 | Heating & Cooling
Mar 21, 2009 | Heating & Cooling
Jan 17, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 10, 2006 | AEG B2100-4 Electric Single Oven
Jul 12, 2014 | AmcorAire UCHW-H12AF2 Split System Air...
380 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: