Question about Heating & Cooling
Hello It is IMPORTANT to keep the entire run 1".When you get close to the appliance use a 1"X1/2"X1"bull tee.Right now you need 2.Use a 1"plug at the end for future furnace hook up.You need to maintain 1" for pressure during demand reasons.You can use 1"X3/4X1"bull tee if the appliance(gas valve) takes that size ,you can't go wrong with larger pipe.Install a BALL **** at each tee for service.
Posted on Sep 17, 2010
Testimonial: "Thank you very much! I plan on stepping it down from one inch to three quarter."
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 05, 2016 | Electrical Supplies
Aug 13, 2014 | Heating & Cooling
Aug 17, 2013 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 22, 2012 | Electrical Supplies
Sep 30, 2012 | Electrical Supplies
Jul 27, 2011 | Dayton Heating & Cooling
Feb 03, 2011 | Rheem EcoSense by 7.4 GPM Tankless Water...
Oct 24, 2009 | Forest Natural Gas Fire Pit Black Marble...
73 people viewed this question
Usually answered in minutes!