Question about Heating & Cooling
Hello It is IMPORTANT to keep the entire run 1".When you get close to the appliance use a 1"X1/2"X1"bull tee.Right now you need 2.Use a 1"plug at the end for future furnace hook up.You need to maintain 1" for pressure during demand reasons.You can use 1"X3/4X1"bull tee if the appliance(gas valve) takes that size ,you can't go wrong with larger pipe.Install a BALL **** at each tee for service.
Posted on Sep 17, 2010
Testimonial: "Thank you very much! I plan on stepping it down from one inch to three quarter."
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 05, 2016 | Electrical Supplies
Aug 13, 2014 | Heating & Cooling
Aug 17, 2013 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 22, 2012 | Electrical Supplies
Sep 30, 2012 | Electrical Supplies
Jul 27, 2011 | Dayton Heating & Cooling
Feb 03, 2011 | Rheem EcoSense by 7.4 GPM Tankless Water...
Oct 24, 2009 | Forest Natural Gas Fire Pit Black Marble...
73 people viewed this question
Usually answered in minutes!