Question about Computers & Internet
If you battery life has cross 10 months its probably dead change your battery.
Posted on Mar 13, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: no output 230v ac from
Good day,this type of problem could be caused when your ups is overloaded, it tends to damage the power transistor responsible for converting direct current (DC), to alternating current (AC),the other reason should be , if the output relays or contactors malfunction, these are the possible problem, you will need to visit a service center
Posted on Mar 12, 2011
Tips for a great answer:
May 04, 2014 | Computers & Internet
May 03, 2014 | MGE Computers & Internet
Mar 11, 2011 | Computers & Internet
Dec 24, 2010 | TriPro Power : UPS Pro 650VA (PSTP06) UPS...
Oct 11, 2010 | Belkin (F6C1500-TW-RK) (F6C1500TWRK) UPS...
Feb 07, 2010 | Powercom King Pro UPS System
Jun 22, 2009 | Computers & Internet
Mar 04, 2009 | Opti -UPS PowerES 1400 UPS System
389 people viewed this question
Usually answered in minutes!