Question about Tools & Hardware - Others
I fixed my 3 blinking issue: I pulled off the small blower motor above the vacuum sensor and spun the fan with my finger. It had resistance at first but then it spun freely. I put everything back together and it ran. I figure next year I may have to buy a new motor, but I made it this year. By the way that fan creates the vacuum to allow the sensor to work. It is a safety thing I figure. If the fan seizes up again the unit will sense it and shut down.
Posted on Nov 10, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
if you know what the flame sensor is try gently cleaning it with sandpaper they get gummed up sometimes and don't sense the piolet flame, if they don;t see a piolet it will not allow it to kick the gas on
Posted on Oct 10, 2009
One flash mean ignition failure. The sequence is: T-Stats calls for heat, inducer motor comes on, igniter glows orange (look through glass), then gas comes on and burner lights, approximately 1 minute later the indoor blower comes on. If you don't see the glow, most likely the igniter is bad. If you see the glow but no flame, it's a gas problem, supply or defective valve.
Posted on Dec 31, 2009
Tips for a great answer:
Jan 15, 2015 | Coleman 7990-319p Evcon Gas Furnace...
Feb 14, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Jan 08, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Nov 26, 2013 | Coleman 7990-319p Evcon Gas Furnace...
Jan 25, 2013 | Coleman 7990-319p Evcon Gas Furnace...
Dec 03, 2009 | Heating & Cooling
Aug 14, 2017 | Craftsman Tools & Hardware - Others
368 people viewed this question
Usually answered in minutes!