Question about Pentair Minimax NT Heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Pool heater will not heat
Im no pro, but I know there is an air sensor behind the main board. If the fan is running you probably have a problem with that sensor. If your lucky the air hose could have just popped off.
Posted on Apr 04, 2009
This is a fan falure code. It can mean the fan has problems (not likley if the fan goes and isn't labored) You have a sensor in your exaust (probally not this if you don't get a good start) The culperet is probally in the negetive pressure sensor. This is a 2-3 inch disc with wires going to the controls and a rubber tube going to the fan. Pull the tube from the fan and make sure the fan fitting is clear (poke with a tooth pic) Be sure their are no kinks in the hose. If the heater is 4 years old the diaprahm could be bad in the pressure sensor. Check the other things first but this is probally your problem. Good luck, hope this helped.
Posted on Jan 26, 2010
SOURCE: error code e04
If the fan was seized, it is likely bad, even if you freed it. If it doesn't sound the same, or is not as loud as it used to be, it is also most likely bad. If it doesn't move enough air to close the air pressure switch, then you will get an 04 fault, which is an air flow fault. HTH
Posted on May 24, 2010
For most pool heaters, if they will not start up in the spring, the problem is corrosion in the wiring somewhere... I would remove and clean all wiring connections and then try. The amount of current is very small and so any bit of corrosion can cause the unit not to work.
It all so could the t-stat again, but you would need to check that with an OHM meter. No continuity when the heater should be on will confirm that the t-stat is bad...
Posted on May 14, 2011
Tips for a great answer:
Aug 04, 2014 | Pentair Minimax NT Heater
Jul 07, 2014 | Pentair Minimax NT Heater
May 23, 2010 | Pentair Minimax NT Heater
Oct 01, 2009 | Pentair Minimax NT Heater
Sep 16, 2009 | Pentair Minimax NT Heater
Aug 01, 2009 | Pentair Minimax NT Heater
134 people viewed this question
Usually answered in minutes!