Question about Goodman CLQ36AR49 Air Conditioner
Do you have any frost on the lines going to the outside unit. If the large line is frosted your evaporator (Cooling coil in the furnace) could be frozen up. Operating it with the fan in automatic with the cooling on will sometimes be the cause of this condition.
If there is not frost on the large line going to the outside unit and you are getting air circulation inside the house the problem could be a loss of refrigerant charge. Look at the joints where the pipes were soldered to the inside and outside units for signs of oil. If you find oil at any point it is the indication of a refrigerant leak.
Posted on May 17, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 12, 2012 | Goodman Heating & Cooling
Sep 06, 2011 | Goodman CKL36AR36 Air Conditioner
Aug 08, 2011 | Goodman CLJ36AR42 Air Conditioner
Sep 11, 2010 | Goodman CKL60AR60 Air Conditioner
Aug 11, 2009 | Heating & Cooling
Jul 29, 2009 | Goodman CKL60AR60 Air Conditioner
Sep 15, 2008 | Goodman Heating & Cooling
Mar 07, 2007 | Goodman CLQ36AR49 Air Conditioner
140 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: