Question about Carrier 38CKC024 Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It sounds like your condenser fan motor may be locked up or the capacitor that helps give the condenser fan motor a kick to get it started may be defective. Try turning your system on and using a long screwdriver try to push the fan blade on the condenser fan motor to see if it will run normally if you give it the starting boost it needs.If it does run at full speed and doesn't over heat or start and then slow down then you probably only need to replace a simple 10-12$ capacitor. If it barely turns, makes an odd humming sound or overheats etc. then you will have to replace the condenser fan motor. This is assuming that the outdoor condenser has the 220v supplied and the 24v supplied to the compressor relay, that the compressor relay is engaged and suppling 220v to the condenser fan motor.
Posted on May 30, 2008
is this unit real old ? it does not come up in my book . the btu is 30000 that is the same as 2.5 ton it may be 6,7 or 8 seer i dont think its a 10 seer because the 10 seer units are listed and yours is not . if this sounds wrong please look up the mod # again and post the ser # too ......... Please if this answer helped , please rate this 3 or 4 stars . and keep me in the paid answer department . A 1 or 2 may knock me down into the unpaid ranks. Thanks Cactus Bob .
Posted on Mar 15, 2009
567C024RCU In this model number is the # 24. That stands for 24,000 btu's. This is a two (2) ton unit. Has this two ton unit cooled ok in the past? if so replace with the same size. But make sure yo change the indoor coil to match the size "and" efficiancy of the ew unit.
Posted on Apr 14, 2009
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
Tips for a great answer:
Aug 02, 2012 | Carrier 38CKC036 Air Conditioner
Jul 08, 2012 | Carrier 38CKC036 Air Conditioner
Aug 27, 2011 | Carrier 38CKC024 Air Conditioner
Jul 25, 2011 | Carrier 38CKC024 Air Conditioner
Jul 05, 2011 | Carrier 38CKC024 Air Conditioner
Jun 20, 2011 | Carrier 38CKC042 Air Conditioner
Jun 02, 2011 | Carrier 38CKC024 Air Conditioner
Mar 01, 2011 | Carrier 38CKC042 Air Conditioner
May 16, 2010 | Carrier 38CKC060 Air Conditioner
Mar 15, 2009 | Amana Comfort Zone 12M32PBEH Air...
266 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: