Question about Intertherm Heating & Cooling
The entire unit will not come on at all. The air compressor, fan, heat are not working. It does have power to it.
Do you have a low voltage fuse in the Air Handler?
The fuse could have blown if there is a low voltage short in the system. The low voltage system powers the Thermostat.
If no fuse the transformer may be bad. Or the Thermostat may be bad. Or it could be a tripped float swith which means the drain line is plugged and overflowing the primary pan into the secondary pan. Nothing runs if the installer broke the red wire to the switch. It's always a good idea to keep the drain line clear. this can be done by finding the location to where it comes out on the outside of your house. use a wet and dry vac on the line or even back flush with a garden hose just make sure you use a very short count to 5 when flushing. You do not want to flood the primary pan you just want to cause a vaccume on the line with water.
Posted on May 17, 2008
SOURCE: my a/c unit will not come on
If you have a digital thermostat check the battery. After you change the battery switch the fan to the on position. The fan should come on. If it does not the transformer that supplies the voltage for the control circuit could be bad. Check the fuse at the air handler and the off/on switch also to make sure it is on at the air handler (Furnace).
Posted on May 17, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 20, 2014 | Dometic Rooftop RV Air Conditioner
Jul 06, 2014 | Goodman CLQ36AR49 Air Conditioner
Jun 07, 2013 | GE Zoneline AZ55H07D Air Conditioner
Since the failure of an air conditioner to turn on, loss of air conditioner cooling capacity, reduced air conditioning output temperatures, loss of cool air supply, or even loss of air flow entirely can be due to a variety of problems with one or more components of an air conditioner or air conditioning system, after reviewing the lost air conditioner cooling diagnosis procedures described in this article, be sure to also review the diagnostic procedures at each of the individual air conditioning diagnosis and repair major topics listed just below. To return to our air conditioning and refrigeration home page go to AIR CONDITIONING & HEAT PUMP SYSTEMS.
Electrical problems on HVAC systems: Keep in mind that despite the depth of technical detail you will find here about all components of air conditioners and heat pumps, most service calls for non-working air conditioners or heat pumps turn up an electrical problem. So if your A/C system is just not working at all be sure to check all of our electrical and control setting suggestions first.
Mechanical problems on HVAC systems: tend to fall into these groups: refrigerant leaks, dirty condenser coil or unit, dirty evaporator or cooling coil, or burned out (or hard-starting) compressor motors. We have also seen a number of problems with fans and fan motors in both the compressor/condenser unit and in the air handler/blower fan unit. Some of those fan problems are mechanical - like a loose fan belt or blade. MORE DETAILS
Nov 13, 2012 | Heating & Cooling
Aug 21, 2011 | Ruud UBHC Air Conditioner
Aug 09, 2011 | Haier HD656E Dehumidifier
Jun 21, 2010 | Carrier 38CKC036 Air Conditioner
Sep 01, 2009 | Kenmore Refrigerators
May 16, 2009 | Fujitsu 24R1 Air Conditioner
May 17, 2008 | Heating & Cooling
92 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: