Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
The combustion air switch is closed by the air pressure from the draft inducer fan. You can check it with a voltmeter. When the heater starts to run check the voltage reading where two wires connect to the switch. It should be 0 vac if the switch is closed. Instead of starting the furnace, you could also remove one end of the rubber hose that goes to it from the draft motor and blow into the hose and see if that closes the switch. It may be just stuck. I almost forgot to mention the most important thing; make sure the draft motor is running. Let me know what you find. The air pressure switch is a safety feature to prevent the furnace from running if there isn't enough air supplied to the burner for proper combustion.
Posted on Sep 16, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 14, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Nov 11, 2012 | Coleman Propane Forced Air Heater...
May 09, 2012 | Coleman Propane Forced Air Heater...
Sep 16, 2011 | Heating & Cooling
Mar 07, 2011 | Heating & Cooling
Oct 02, 2010 | Heating & Cooling
Oct 04, 2009 | Heating & Cooling
Oct 03, 2009 | Coleman Propane Forced Air Heater...
May 15, 2014 | Coleman Propane Forced Air Heater...
1,262 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: