Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
For Trane sytems, B is your "Common" wire. O is your reversing valve relay, G is your fan, Y is your compressor contactor, R is Hot, Brown will not be used on your electronic tstat. X2 is your backup electric heaters. Without knowing what terminals are on your new tstat, I cannot offer more information than this. The installation manual may indicate what each terminal is controlling. I strongly suggest to write down ALL of the terminals and colors from your old t-stat and be sure to turn off the power to your air handler. Put the fan switch on your tstat to ON before turning off the power. Make sure the fan is running. Then turn the power off to your Air Handler. If your fan stops running, you have turned the power off to your tstat and are ready to start replacing it with your new tstat. I hope you find this helpful. Good Luck!!!
Posted on Feb 07, 2010
Tips for a great answer:
Aug 17, 2016 | Heating & Cooling
Feb 03, 2016 | American Standard Heating & Cooling
Aug 17, 2014 | Heating & Cooling
Apr 20, 2017 | Omega Trane Furnace Draft Inducer Blower...
Feb 06, 2010 | Heating & Cooling
Jun 25, 2009 | Omega Trane Furnace Draft Inducer Blower...
Jun 02, 2009 | Carrier Heating & Cooling
May 16, 2009 | Heating & Cooling
Mar 22, 2009 | Honeywell Programmable Thermostat Heater
Aug 21, 2017 | Heating & Cooling
316 people viewed this question
Usually answered in minutes!