Question about Honeywell Heating & Cooling
Hello A couple of things.If burner is cycling on high limit ,it can be a air flow problem.Change the air filter.Check the blower wheel that is reasonbaly clear/clean.Also check the intake grille that it is not blocked and all the supply grilles are open.Also mabey the nozzle size can be steped down if the input is too high(a slightly smaller fire).If the blower fan on/off is the problem (as the burner is seperate) raise the 120*f pin to 130*f but hold the wheel disc steady during adjustment.Leave the 90*f at 90*f.
Posted on Sep 15, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 09, 2015 | Heating & Cooling
Aug 24, 2014 | Heating & Cooling
May 02, 2011 | Goodman GMS90703BXA Heater
Mar 15, 2011 | Ruud Heating & Cooling
Dec 20, 2010 | Heating & Cooling
Nov 25, 2010 | Heating & Cooling
Nov 22, 2010 | Goodman GDS80904BNA Open Flame Heater
Dec 04, 2009 | Refrigerators
Oct 19, 2009 | Holmes Products HCH4062 Ceramic Compact...
Jan 05, 2009 | Honeywell L4064B2236 Fan/Limit Control...
198 people viewed this question
Usually answered in minutes!