Question about Ruud UAKA030 Air Conditioner
I have a UAKA-037JA Ruud AC unit. I just bought the house. No one has lived in the house for about 2 years. When I turn on the t-stat to cool the unit just buzzes. Air is coming out of the vents but the unit is not cooling. I pulled the service panel to see if anything looked wrong. I didn't find anything. Is some part of the unit shot?
Is the buzzing in the outdoor half of the system? If so
your possibilities are.
buzzing could be the contactor. In the control compartment on the side of the unit there is a small brown component that has wires to one side and the other . There are contacts in the center like points on a car. If the points are pulled in look for ants in between the contacts. Always secure power to the outdoor unit before touching anything inside. If the points are pulled in check your breaker to the outdoor unit. Turn the breaker off then back on. Breakers sometimes trip but look ok.
Buzzing could be thee coil to the contactor itself, sometimes with age the coil will breakdown and cause noise.
if you give me more information I can focas in closer to a solution
Posted on May 16, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 17, 2014 | Ruud Heating & Cooling
Aug 03, 2011 | Ruud Heating & Cooling
May 02, 2011 | Ruud UAKA048 Air Conditioner
Apr 29, 2011 | Heating & Cooling
Jul 03, 2010 | Heating & Cooling
Jun 15, 2010 | Ruud UAKA037 Air Conditioner
May 08, 2010 | Ruud UAKA030 Air Conditioner
Aug 10, 2009 | Ruud UAKA037 Air Conditioner
Jun 05, 2009 | Ruud UPMC036 Air Conditioner
Jul 17, 2008 | Ruud UBHC Air Conditioner
192 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: